A. Unless surface transformers are isolated by elevation (eight feet or more above the ground), they shall be enclosed in a transformer house or surrounded by a suitable fence at least six feet high. If the enclosure or fence is of metal, it shall be grounded effectively. The gate or door to the enclosure shall be kept locked at all times, unless authorized persons are present.
B. Surface transformers containing flammable oil and installed where they present a fire hazard shall be provided with means to drain or to confine the oil in the event of rupture of the transformer casing.
E. No electrical work shall be performed on low-voltage, medium-voltage, or high-voltage distribution circuits or equipment, except by a certified person or by a person trained to perform electrical work and to maintain electrical equipment under the direct supervision of a certified person. All high-voltage circuits shall be grounded before repair work is performed. Disconnecting devices shall be locked out and suitably tagged by the persons who perform electrical or mechanical work on such circuits or equipment connected to the circuits, except that in cases where locking out is not possible, such devices shall be opened and suitably tagged by such persons. Locks and tags shall be removed only by the persons who installed them or, if such persons are unavailable, by certified persons authorized by the operator or his agent. However, employees may, where necessary, repair energized trolley wires if they wear insulated shoes and lineman’s gloves. This section does not prohibit certified electrical repairmen from making checks on or troubleshooting energized circuits or the performance of repairs or maintenance on equipment by authorized persons once the power is off and the equipment is blocked against motion, except where motion is necessary to make adjustments.
Code 1950, §§ 45-82 to 45-82.2; 1954, c. 191; 1966, c. 594, §§ 45.1-76, 45.1-78; 1993, c. 442; 1994, c. 28; 1996, c. 774; 1999, c. 256; 2005, c. 3.